How easy is it to obtain NO4I? New are no longer continuously manufactured, and therefore supply is scarce. However, at AoteWell Automation we specialize in sourcing hard-to-find products, and although the lead time varies, the average is between business days. What is the typical price for the NO4I?
|Published (Last):||27 May 2013|
|PDF File Size:||19.38 Mb|
|ePub File Size:||20.22 Mb|
|Price:||Free* [*Free Regsitration Required]|
When you say that you are 5 bits off the expected value, do you mean that, for example, when you are expecting an unscaled value of binary you get a value of binary? First I would use different power supply than the AB for loop power. Double check all the loops, their rspective shielding and such. Rockwell Automation You may find the solution manula be using a seperate power supply to power the analog loops.
They are not precision instruments. I have never ever done that and have never had problems. Watch an animation of a conveyor stacking operation demonstrating the use of a move on a gear command. By David no4i on 9 March, — 9: As i recall the 24V user supply coming from the AB slc power supply is not regulated. If your power supply is supplying another devices try to use an external power supply only supplying your transmitters.
How many transmitters are run off the power supply? Your subscription request is being processed. If not you might want to disconnect each individual analog and reland one at a time and see if there is one that is causing problem and try with and without an optical isolater on each point.
Attached only at the PLC end? What are the wire lengths involved? Just a few things to check, David. The N14 Analog Input module contains 4 analog input channels that are user selectable per channel for voltage or current to support a variety of monitoring and controlling applications. By Bob Peterson on 9 March, — 8: Well, what if you were able to see a piece of equipment before you purchased it? Is the problem apparent on all analog inputs or just a few? Grounding, shielding, bad PS.
Ground loops can be a problem if attached at both ends. Stock Quick Quote. Related Posts.
Allen-bradley SLC 500 1746-NO4I Manuals
Give us a call at or We can help you with your Revision specific needs. Close What is New Surplus? Close What is Surplus New? Surplus New - New unused and includes all sub-assemblies and documentation.
Allen-Bradley 1746-NO4I I/O Module, Analog, Standard, 4 Channel Output, 24VDC
1746-NO4I MANUAL PDF